Treating Mine Water to Reduce Environmental Impact
Acid Mine Drainage Treatment
The discharge of dangerous contaminants generated through mining processes can heavily impact the environment. Sedimentation and filtration technologies help clarify water that contains suspended solids and treat water with dissolved chemicals or minerals.
Our treatment solutions meet regulatory compliance for the disposal of water that could contain arsenic, cyanide, selenium, or other heavy metals and suspended solids. WesTech solutions address treatment for acid mine drainage, neutral mine drainage, and acid rock runoff.
Solutions and Applications for AMD
Acid Mine Drainage
Acid mine drainage (AMD) is typically characterized by low pH and high dissolved iron. The acid mine drainage may also contain high amounts of CO2, which forms carbonic acid and further depresses the pH.
There are four chemical reactions that represent the chemistry of pyrite weathering to form acid mine drainage. An overall summary reaction is as follows:
2 FeS2+7 O2+2 H2O → 2 FeSO4-+2 H2SO4
Pyrite + Oxygen + Water → Ferrous Sulfate + Sulfuric Acid
The acid mine drainage waste is characterized by red water. The simplest treatment is neutralization and clarification. The ideal neutralization first combines one of the reactants with previously precipitated solids. This blend is then mixed with the other reactant. This seeding provides the opportunity for crystal growth.
It also significantly reduces the reaction time. The final pH range of most neutralization reactions is 6-9. Many heavy metals precipitate as hydroxides within this pH range. However, if these heavy metal hydroxides are subjected to a pH > 11.5 for a few minutes, they convert to a crystal-like particle that clarifies, thickens, and filters more effectively than the original hydroxide.
The most commonly used neutralization agent is lime. Lime is added to previously precipitated solids in a blend tank, commonly called the densification tank. The neutralization flowsheet with this high pH feature is a high-density sludge (HDS) flowsheet.
Excess CO2 dissolved in the acid mine drainage stream can be stripped out using a surface aerator. Lowering the CO2 levels can raise the pH as much as one point and lower the amount of lime required for pH adjustment. This step also begins to oxidize iron and manganese and assists in their precipitation.
After stripping, the HDS slurry from the densification tank and the acid mine drainage stream are mixed in the reaction/aeration tank(s). The combination of aeration, high pH, and mixing causes the iron, manganese, and other heavy metals (if present) to precipitate to the fullest extent possible at the set pH level.
Treated water flows to a thickener for sludge thickening and clarification of the water. The metal precipitates as sludge, and a portion of the sludge is recycled to the sludge densification tank. The remainder of the sludge goes to disposal. Generally, the sludge will also contain gypsum and unreacted lime, which enhance the resistance to re-acidification and metal mobilization. A gravity sand filter may be used to polish the stream prior to discharge, depending on permit limits.
Depending on the site conditions, the thickened waste sludge may be redirected to another portion of the mine, dewatered and deposited prior to disposal in a landfill, or concentrated to paste and stacked.
Since acid mine drainage comes from abandoned mines these sites are often in mountainous, uninhabited areas where access to the site may be difficult. Many systems have been built with ease of operation being paramount. In fact, the systems are often built for operation with no onsite operator. This has led to the use of caustic for neutralization. Caustic is a liquid and is much easier to feed than lime. However, it does not make the same crystals that lime does, so the precipitate is difficult to settle. Caustic-fed systems are much more liable to upsets and the precipitation tanks should be designed for longer holding times. Also, caustic is much more expensive than lime.
High-Density Sludge (HDS) Treatment
WesTech HDS circuits are designed for high density solids removal. A typical system involves several steps. These are accomplished in a series of mix tanks followed by a HiFlo™ high-rate thickener. A typical high-density sludge circuit would entail the following process steps:
- The pH of the underflow is raised using lime and allowed to fully react.
- The high pH underflow is mixed with the fresh feed and again allowed to react.
- The mixture is settled in a thickener.
- The underflow is recycled back for lime addition.
- A portion of the underflow is released as waste.
Low Total Dissolved Solids (TDS)
While the majority of waste streams generated from acid mine drainage (AMD) are characterized by low pH (2-4) and high dissolved iron (1,000-10,000 ppm), there are some AMD streams that are not contaminated to these extremes. These streams may have relatively high pH levels (5-7) and dissolved iron levels as low as several hundred ppm.
With water sources from industrial applications, especially hydraulic fracturing (fracking) operations, becoming harder to obtain, these marginal quality water streams are becoming more attractive for reclaim and use as process makeup waters.
Depending on the quantity of water required, water quality of the existing mine pools, and the water quality required for the process, there are a number of treatment options.
Dissolved ferrous iron (Fe2+) is first oxidized to ferric iron (Fe3+), which readily forms the insoluble iron hydroxide complex Fe(OH)3. In addition to providing the oxygen required to precipitate the iron, the use of surface aerators allows CO2 to be stripped from the water. This increases the pH of the water stream as well.
In the case of these relatively small flows, caustic (NaOH) is used as the sodium hydroxide source. Caustic, while having its own hazardous properties, is easier to prepare and add to the stream, involves less capital cost, and produces less sludge than the addition of lime slurry, which is commonly used on large AMD flows. The caustic also increases the pH to a neutral level for further treatment and subsequent use.
Polymer is added to the stream to aid in floc formation and the stream is subjected to high energy mixing either in an inline mixer or a rapid mix tank. This is done to ensure that the polymer solution is completely dispersed in the stream. The flow then enters a slow mix tank, which allows the floc that is beginning to form to grow to a point where it is large enough and heavy enough to readily settle.
SuperSettler™ Inclined Plate Clarifier
A WesTech SuperSettler™ lamella type unit can be used for this purpose. This unit provides a large projected area in a relatively small footprint. In addition, it has no moving parts, making for easy operation and low maintenance. Solids settled in the lamella section are collected in a bottom hopper. This hopper can have a thickening mechanism or rake added as an option to thicken the sludge.
SuperSand™ Continuous Backwash
The SuperSettler is perfectly coupled with a SuperSand™ continuous backwash sand filter. This is due to the fact that the water can flow through both units without having to be repumped. The SuperSand unit creates its own filtered water backwash stream so there is no need for filtered water storage or backwash pumps. The unit generates a constant dirty backwash stream of approximately 3-5 percent of the inlet flow.
If low TDS water is required for downstream processes (i.e., boiler feed), then ultrafiltration and reverse osmosis can be added to the system to produce this type of high-quality effluent.
Depending on the mine site, the waste streams from each treatment step may be returned to a separate section of the mine for disposal. At installations where this is not possible due to either logistics or regulations, conventional sludge thickening and dewatering technologies may be applied.